Q: We have a construction project in our cafeteria. We have an ILSM and additional measures in place. However, it was determined last week that we need to remove the sprinklers in the area for eight weeks. The construction is located on the lowest level and is unoccupied with no patient care in the area (but there's patient care in the building). With the sprinklers out of service 24 hours a day, is a fire watch required? We also are looking at using 1 hour barriers and 3/4 hour doors during that time. Do the barriers change anything with a fire watch? Thank you
A: Can’t you re-install temporary sprinklers in this construction area for the duration of the project? You will need to turn the sprinkler lines upward to within 12 inches of the deck and install upright sprinklers. It is imperative that you have sprinkler protection, otherwise you will need to conduct a fire watch, continuously for the 8 weeks there are no sprinklers.
Yes... a fire watch is required because you have impaired sprinklers. It doesn’t matter where the impaired sprinklers are located… if you have impaired sprinklers, you must do a fire watch. NFPA 25-2011 section 15.5(4) says where the sprinkler system is out of service for more than 10 hours in a 24-hour period, you need to conduct a fire watch. CMS has said in their Final Rule published May 4, 2016, that a fire watch is conducted continuously, without interruption. The designated individual who performs no other function, continuously walks the impaired area looking for fire and the potential for a fire to occur, without leaving the area. This means the individual may not leave the impaired area to use the restroom, take a lunch break or any other function unless he is relieved by someone else.
This ‘continuous’ fire watch must be conducted for the duration that the sprinklers are impaired … 8 weeks. Can you afford to have that many FTEs designated to do nothing else but a fire watch for 8 weeks? I would believe it would be less expensive if you would turn up the sprinklers and install upright sprinkler heads in the construction area.
The fire watch does not affect the rated barrier, but the 1-hour fire rated barrier is required to separate the construction area from the occupied area if there are no sprinklers in the construction area.
Brad Keyes, CHSP, is the owner of KEYES Life Safety Compliance, and his expertise is in the management of the Life Safety Program, including the Environment of Care and Emergency Management programs
See the latest posts on our homepage